Get the system you need.
Audio and visual nurse call systems for assisted living facilities, nursing homes, hospitals and outpatient medical clinics.
Traditional lights, buttons and pull cords are smartphone/WiFi integrated. Let us know what you’re trying to do and we’ll take care of you.
Order by Noon CST for possible same day shipping*
*See Terms & Conditions
Need Some Assistance?System Quote System Design/Installation 1-800-558-8957
Remote Monitor Panel
(1-800-558-8957) Call for Price 1-800-558-8957
Remote Control Panel (A-1700 Series) consists of anodized aluminum face plate, surface-, flush- or desktop-mountable. Steady green LEDs indicate unarmed status; steady red, armed status; flashing red with intermittent tone, an alarm condition. Zones are designated via plastic-covered designation strips.
Used with the CORNELL Series A-1000 Door Monitor Systems, A-1700 panels with integral LEDs permit remote monitoring of individual zones within the system.
Tone volume is adjustable via high-low switch.
The contractor shall furnish and install CORNELL A-1700 Remote Monitor Panels as shown on the plans for use with series A-1000 Door Monitor System. Each (flush-) (surface-) (desktop-) mountable panel shall accommodate zone circuits. Indicators shall be LEDs; incandescent lamps are not acceptable. Steady green LED shall indicate unarmed status; steady red, armed status; flashing red with intermittent tone, and alarm condition. Zones shall be designated with plastic-covered designation strips. Power shall be derived from the A-1000 master panel at 12 volts DC, regulated. Each remote zone indication requires 17mA.
- Power Requirements: 12VDC
- Operating Environment: 50-120°F Indoor Non-condensing
- Mounting: Surface, Flush, or Desktop
- Wiring: #22 AWG Minimum
Get Help with System Design/Installation
Download Brochure & Wiring Diagram