Get the system you need.
Audio and visual nurse call systems for assisted living facilities, nursing homes, hospitals and outpatient medical clinics.
Traditional lights, buttons and pull cords are smartphone/WiFi integrated. Let us know what you’re trying to do and we’ll take care of you.
Order by Noon CST for possible same day shipping*
*See Terms & Conditions
Each station features one red and one green LED. Arm and disarm functions are operable via spring-return, center-off toggle switch when key switch is in “enable” position. Stations feature single-gang stainless steel faceplate with silk-screened designations. They may be flush mounted on standard outlet boxes with single-gang rings, or surface mounted on Wiremold 5748 or equal with a depth requirement of 1-3/4”.
A-1800 Remote Zone Control stations provide authorized personnel with access to doors controlled by the Series A-1000 Door Monitor System. Arm and disarm functions are manually controlled via toggle switch and key.
Tone option available on two gang plate.
The satin finish stainless steel faceplate with silk-screened designations may be flush mounted on a standard outlet box with single-gang plaster ring, or surface mounted on a Wiremold 5748 or equivalent.
The contractor shall install CORNELL A-1800 Zone Control Stations for authorized access to individual doors in the Series A-1000 Door Monitor System. Each single-gang stainless steel station suitable for (flush) (surface) mounting shall feature a red and a green LED, with green indicating unarmed status, red indicating armed and flashing red indicating alarm condition. Key switch and spring-return, center-off toggle switch shall be standard, with arm and disarm functions controllable only when key switch is in “enable” position. Power shall be supplied via the Series A-1000 master panel at 12 volts DC, regulated. Current is 17mA per station.
- Power Requirements: 12VDC
- Operating Environment: 50-120°F Indoor Non-condensing
- Physical Faceplate Dimensions: 4 ½ ”H x 2 ¾ ”W (1 Gang)
- Mounting: Single-Gang back box with 1¾” minimum depth
- Wiring: Terminations are Pigtailed